How can I configure SIPLUS extreme modules (order no.: 6AG1 ...) in STEP 7?
You have a SIPLUS extreme module for extreme environment conditions with order number 6AG1 ... and would like to configure it with STEP 7.
For this you use the type based on this module with order number 6ES7 ... .
The following excerpt from the STEP 7 HW Config shows the configuration of an ET200M of SIPLUS extreme:
Slot 2: IM 153-1 with order number: 6AG1 153-1AA03-2XB0
Slot 4: SM 321 16DI with order number: 6AG1 321-1BH02-2AA0
Slot 5: SM 322 16DO with order number: 6AG1 322-1BH01-2AA0
Fig. 1: Sample configuration of an ET200M of SIPLUS extreme
More information is available at www.siemens.com/siplus or in Entry ID: 18607092
If you were previously implementing SIMATIC Outdoor modules (6ES7 ...-...8.-....), you replace them in specific cases with SIPLUS extreme modules without having to reconfigure. For example, you can replace the following modules with an ET200M with order number 6AG1 153-1AA03-2XB0 (SIPLUS extreme) in a spare parts case without reconfiguration:
- 6ES7 153-1AA03-0XB0
- 6ES7 153-1AA83-0XB0
- 6ES7 153-1AA02-0XB0
- 6ES7 153-1AA82-0XB0
An overview of all the order numbers of the relevant SIMATIC, SIMATIC Outdoor and SIPLUS extreme modules is available in Entry ID: 17054970